There are three basic requirements:
- Level Floor
Each Midas XCI™ tank is self-contained and can be added individually for flexibility as you grow.
Midas Green Technologies offers an exhaustive list of installation and planning guidelines in our Product Support section.
Each Midas XCI™ tank requires 8.6 m2 (28 ft2) for the tank and redundant cooling modules. We recommend a minimum of .6 m (2 ft) at the front and back of each tank to allow room for maintenance and access.
Floor Loading Requirements
Midas XCI™ will need to be installed on a level floor with a recommended minimum floor loading capacity of at least 17.24 kPa (2.5 psi).
Midas XCI™ can operate as a stand-alone system, however to take full advantage of all the features and analytical information, we recommend an Ethernet connection (Cat5E or better) with one IPv4 Address per cooling module (Max two per tank).